Industry Articles Display
2021-05-12 Control Engineering
Webcast teaches power system harmonics and best practices for harmonics mitigation and their relationship to IEEE 519, which guides the design of power systems with non-linear loads. The 2014 revision of IEEE 519 clarified language subject to interpretation and misinterpretation.
By: Larry Gardner and Christopher Jaszczolt
- Learn about harmonics, the problems resulting from harmonics, their causes and cures.
- Examine the advantages and disadvantages of various harmonics mitigation techniques.
- See how a new VFD technology can avoid the need for other harmonics mitigation.
Power system designs often need to mitigate power harmonics that can harm connected commercial and industrial equipment. The 2014 version of IEEE 5019 provides recommended practice to guide in design of power systems with non-linear loads. A May 25, 2021, webcast, “Power system harmonics: Mitigation practices and technologies,” provides a harmonics overview, changes to IEEE 519 and offers harmonic solutions. Key points follow.
Harmonics 101: industrial, commercial
The webcast offers a bit of harmonics 101 to set the stage for discussion of IEEE 519 and what it means for harmonics, various means of harmonics mitigation and the advantages and disadvantages of each, and a variable frequency drive (VFD) technology the requires no mitigation for harmonics.
VFDs save motor energy, save money, reduce wear and tear, and improve control performance. VFDs draw current in a non-sinusoidal way resulting in current harmonics, along with other commercial and industrial equipment and devices. Conventional VFDs use input rectifiers to convert incoming three-phase ac power to dc, and store that dc power in capacitors, referred to as a dc bus. The business end of the drive then uses high-speed switches to to send pulses of voltage to the motor. The switches, called insulated gate bi-polar transistors (IGBTs), turn on and off in a sequence the motor interprets as a sine wave. By varying the frequency of the pulses, the VFD can vary the speed of the motor.
Harmonics occur when the current waveform is distorted.